Mike the Boilerman
Your independent Boilermate specialist based near Hungerford, Berkshire
For more information or to book your breakdown repair, call or text me on
How does the original BoilerMate work?
Firstly, if yours doesn’t work, call or text me for advice or for a repair on 07866 766364.
A conventional central heating boiler heats the water in the BoilerMate directly. The stored water is pumped to the boiler for heating and back again by the right-hand of the two pumps on the unit whenever the stored water temperature drops below a specific temperature set in the factory. The left-hand pump circulates the stored hot water around the radiator circuit(s) when the heating controls are calling for heat.
There are two circuit boards behind the cover panel. A pump drive board to run the central heating pump for a few seconds every forty hours to prevent it seizing up over the summer months when it is not in use, and a delay timer to keep the pump running for a short while after the boiler has shut down to extract the residual heat in the boiler heat exchanger.
Heat is transferred into the hot tap water by passing the cold mains water through a coil of pipe inside the unit, immersed in the store of hot water. Heat passes through the wall of the tube and heats the cold mains water on it's way to the hot tap. To control the temperature of the domestic tap water, a thermostatic blender valve mixes in a proportion of cold water. The output temperature can be set by the user.
And what goes wrong with them?
1) Depleted water in the thermal store:
The hot water is only hot when taps are running slowly, and the unit continuously makes a noise like muffled water pouring. This is usually the store being only partly full of water, usually caused by the float valve in the feed & expansion tank on the top seizing up and stopping working. A new float valve fixes this. Occasionally the same fault is caused by a blocked cold fill pipe connecting the F&E tank to the main tank of hot water. The blockage can be extremely difficult to dislodge so with a bit of basic plumbing the blockage is usually best bypassed with a new section of pipe.
2) A loud, random, intermittent buzzing noise:
One or other of the two small PCBs makes this noise when it gets old. Best to replace both PCBs in my opinion as I’ve replaced the noisy one occasionally, only for the customer to call me back a few weeks (or hours) later because the other one is shown up to be buzzing too!
3) Hot water failure when heating works fine:
The coil of pipe immersed in the tank of hot radiator water is so simple it is hard to imagine how it could NOT always work. But it fails sometimes due to water scale lining the inside of it. Chemical descaling will fix this. The blender valve sometimes breaks giving identical symptoms. Easily replaced with a new one.
Thats about it really. Not a great deal to go wrong with this simple model. If your Boilermate original has stopped working, do call or text me to discuss a repair, on 07866 766364.
Boilermate Original in a customer’s house - very few of these left now
Copyright Michael Bryant 2022
Site first created 21st January 2007
Site last updated 2nd April 2022
Gas Safe Register 197499. CIPHE reg no 56207